VapourTreatment (For controlling of Scale & Foam)
This is a highly active antifoulant, water scale inhibitor, dispersant and anti-precipitant compound for use in industrial and marine water systems, such as cooking systems, heat exchangers, air conditioning equipment, etc.
RXSOL-51-6001-025 is a concentrated solution of a POLYELECTROLYTE polymer and antifoaming agents for use in SEA WATER evaporator as a controller of scale and foam in side the evaporators. It can be used as a scale inhibitor in the feed water to EVAPORATORS producing fresh water .
A liquid polymer-based evaporator treatment specially designed to control and prevent scale formation in evaporators
|Appearance Thermal Firmness||Clear yellow liquid 250° C||By keeping heat transfer surfaces free of scale , Ensures that the evaporator works at maximum efficiency.|
|Density||In g/cm3 at 15°C: 1.1||
Permits more efficient evaporation.
|pH (1 Vol%)||9||
Reduces downtime and maintenance costs.
|Compatibility||Concentrated, safe liquid, easy and economical dosing.|
|Metal||No known effect||
For use in both high pressure and vacuum evaporators
|Rubber||No known effect||The antifoaming properties ensure that distillate quality is high|
20 / 25 ltr
Improves the quality of distilled water
Procedure Of Use and Dose Rates: POLYELECTROLYTE polymer of RXSOL-51-6001-025 reacts with the potential scale forming salts in the water to prevent them from adhering to heat transfer surfaces. These solids are held in suspension and easily removed from the evap -orator line .Finally RXSOL-51-6001-025 also have defoaming properties by which will stop foaming in EVAPORATOR.And by that way Distilled water quality is maintained in side the EVAPORATOR.
Used in both high and low pressure evaporators
|Daily Out Put Evaporator||Daily RXSOL VT 6001 Requirement|
|10 – 20 MT||100-200 ML|
|30 %u2013 40 MT||300-400 ML|
|50 %u2013 60 MT||500-600|
Setting the Flow Rate: The treatment is added to the dosage tank and mixed with water. Example: With the 0.5 litres of Vaptreat add sufficient water to make up 50 litres of liquid.The standard flow meter is Adjustable-Rate=0-l00ml/minute.Flow rate calculation: Flowrate = 50 Litres/24 x 60= 35 ml/min setting i.eThis will last 24 hours.
Note: We can remover existing mineral scale deposits by using A 5-10% solution of RXSOL-51-6001-020
Note: This article uses material from the http://rxmarine.com/